 Industrial Ventilation Physics Chapter 7 Exercise Questions Help

anvspbq

Writing

### Question Description

7 question and i attached ch7 doct

Also i attached ch7 pdf

### Unformatted Attachment Preview

Industrial Ventilation (Chapter 7) 1. The circumference of a round duct is about 37.5 inches. The average velocity pressure (VP) of air flowing in the duct is 0.30 inch w.g. at standard conditions (STP). Please calculate: a) Duct diameter b) Average Vduct c) Air flowrate Q, and compare your Q with that on Chart 5 to determine the difference. 2. The average air velocity pressure (VP) of an airstream in a duct is 0.90 inch w.g. The temperature of the air is T = 75 ℉ and the duct is located 1,000 ft above sea level. What is the actual average air velocity? Hint: you need find B.P. online for df calculation. 3. Standard air (d=1) moves through a galvanized duct system at the velocity (Vaverage) of 5,000 fpm and Dduct is 8 inches. • List the three equations that you use to solve the problem. • Please estimate VP • Please find the loss factors K from the Charts, and then estimate static pressure loss for each component in each branch (a-f). • Please calculate the friction loss for the entire duct system, La-f = 50’, galv duct 1 Component a. Flanged hood (round) b. Plain duct hood (round) c. Elbow, 3-piece, R/D=1.5, 90° d. Elbow, 5-piece, R/D=1.0, 90° e. Elbow, 4-piece, R/D=2.0, 45° f. Branch entry, 60° included angle Friction loss (FL), La-f = 50’, galv duct K or Fh Where can you find the K value? Chart 11A Chart 11A Chart 5 SP loss (“w.g.) FL = 4. Discuss how you can use blast gate method to balance the SP between branches. You can give an example and/or use diagram. 5. A ventilation system has two branches: one branch requires to have SP of – 5.3” w.g. and Q of 4.8 scfm, and the other needs -6.1 “w.g and 5.2 scfm. 1) Determine the governing static pressure for a ventilation system; and 2) Determine the Qcorrect and specify whether the Qcorrect you calculate is for governing or for non-governing branch. 6. There are several limitations when using blast gate method. Please pick one limitation of your interest, and discuss what method(s) YOU can use to solve the potential problem. 2 7. A ventilation system with two branches: one branch requires to have SP of – 5” w.g. and Q of 4.8 scfm. Determine the maximum range of SP for another branch that allow you to determine the governing static pressure without a further design change needed. 3 ...
Purchase answer to see full attachment Student has agreed that all tutoring, explanations, and answers provided by the tutor will be used to help in the learning process and in accordance with Studypool's honor code & terms of service.

## Final Answer Attached.

Your name
Instructor's name
Course
Date of submission
QUESTION 1
1a
circumference = 3.142 D
37.5 inches = 3.142 x D
37.5 /3.142 =D
D= 11.9351 INCHES

1b
V= 4005 x (VP)^0.5
( VP)
V=4005 X (0.5477
(0.30 inch
inchw.g)
wg)0.5
^ 0.5
2193.629 inch / min
1c
Q= average V duct x Duct cross sectional area
area= 3.142 x 5.9676^2
111.8918
111... Xrivaf_We (13519)
University of Virginia Anonymous
Awesome! Made my life easier. Studypool 4.7 Trustpilot 4.5 Sitejabber 4.4